*UPDATED* 8/1 -A tech came out and figured out that the original tech wired the fan to a light switch, so that when the light was turned off in the room, the fan would not turn on either. The new tech re-wired it correctly; however, he didn't put the cover on the junction box either. Rather than call this company again, I put the cover on myself and replaced the rolled insulation that was moved to do the work. Overall, I was disappointed in the work and the price of the job. I will utilize a different electrical company in the future. 7/31 - Upon entering attic to see why fan wasn't running anymore, I noticed that the junction box was not covered, leaving exposed wires and definitely not up to code. I attempted to self-diagnose the issue of the fan no longer working but could not figure it out. I called Electric Today office to have them schedule a tech to come out and resolve the issue. 7/30 - Adam called me in advance of his arrival to let me know he was on his way. He was extremely professional and knowledgable. I was very pleased with the work he did. I will definitely call Electric Today again for future work needed and will request Adam again.